{'fraction_non_alphanumeric': 0.02557544757033248, 'fraction_numerical': 0.0, 'mean_word_length': 5.069767441860465, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 0, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
Specifying transformer winter and summer peak-load limits

This paper presents a methodology for specifying the winter and summer peak-load limits for substation transformers that carry a temperature-sensitive load, taking into account the random nature of load and ambient temperature as well as their correlation. With this methodology, we can easily and accurately specify the peak-load limits for each substation transformer once the historical ambient temperature and load data are available. Also, we can collectively specify the peak-load limits for the transformer of each cooling type (OA, OA/FA, or OA/FA/FA) in a geographic region based on the mean and standard deviation of ambient temperatures in that region. Such peak-load limits are useful for power system planning.