{'fraction_non_alphanumeric': 0.021705426356589147, 'fraction_numerical': 0.009302325581395349, 'mean_word_length': 5.152380952380953, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 0, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
Power transformer monitoring using UHF sensors: site trials

Sensors operating in the ultra-high frequency (UHF) band have been used to detect internal discharges during site testing of a 1000 MVA oil-filled transformer. The transformer was operated at voltages exceeding normal levels by up to 15%. Two discharge sources were detected at both sensors using UHF test equipment. Discharge signals are analyzed in phase-resolved form and time-of-flight measurements are used to provide further information regarding their origin. The results indicate that the UHF method could prove very effective for transformer testing and online PD monitoring.