{'fraction_non_alphanumeric': 0.02476780185758514, 'fraction_numerical': 0.007739938080495356, 'mean_word_length': 5.400990099009901, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 0, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
Hour‐by‐Hour Analysis for Increased Accuracy of Greenhouse Gas Emissions for a Low‐Energy Condominium Design

The seasonal and hourly variation of electricity grid emissions and building operational energy use are generally not accounted for in carbon footprint analyses of buildings. This work presents a technique for and results of such an analysis and quantifies the errors that can be encountered when these variations are not appropriately addressed. The study consists of an hour‐by‐hour analysis of the energy used by four different variations of a five‐story condominium building, with a gross floor area of approximately 9,290 square meters (m2), planned for construction in Markham, Ontario, Canada. The results of the case studied indicate that failure to account for variation can, for example, cause a 4% error in the carbon footprint of a building where ground source heat pumps are used and a 6% and 8% error in accounting for the carbon savings of wind and photovoltaic systems, respectively. After the building envelope was enhanced and sources of alternative energy were incorporated, the embodied greenhouse gas (GHG) emissions were more than 50% of the building's operational emissions. This work illustrates the importance of short‐time‐scale GHG analysis for buildings.