Automatic Changeover regulators prevent gas outages by switching supply cylinders over to the reserve cylinder automatically when the primary cylinder is near empty. When the primary cylinder is depleted causing the changeover to occur a red indicator will appear signifying the reserve cylinder in now in use and the primary cylinder can be refilled without loss of service. Reduced the damage from the deterioration by metal abrasion, even though use valve often frequencies.
This regulator equipped convert handle which indicates
“serve“ and “reserve”, and diaphragm operation would help adjusting demand pressure. This compact designed for especially space limitation, and light weight helps to easier installation. 


ServiceLiquefied Petroleum Gas (LPG : Liquid Condition)
Max. Capacity 300 kg/h
Inlet Pressure Range (Changeover Pressure + △P ~ 1.56Mpa (15.6 kgf/cm²)
Setting Changeover Pressure0.05 ~0.2 MPa (0.5~2.0 kgf/cm²)
Internal Pressure 3 MPa (30 kgf/cm²)
Inlet / Outlet Connections20K-20A Flange
Inlet / Outlet Length 315mm X 170mm

Adjusting pressure

1. Automatic changeover device equipped two types of spring which allows accurate and comfortable control the demand pressure.
2. Regulator apply pressure range from 0.5 to 2.0kgf/cm², if require to adjust demand
pressure, please check adjusting knob length.
3. To adjust demand control, there is a pressure control screw either turning to clockwise or counterclockwise.
4. Be sure that adjusting knob provides various pressure demands, and suitable pressure has been released.


error: Alert: Content is protected !!