{'fraction_non_alphanumeric': 0.0266129824216832, 'fraction_numerical': 0.015859766277128547, 'mean_word_length': 4.898349261511729, 'pattern_counts': {'":': 0, '<': 1, '<?xml version=': 0, '>': 5, 'https://': 0, 'lorem ipsum': 0, 'www.': 1, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 5, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
Design of Decentralized Adaptive Sliding Mode Controller for the Islanded AC Microgrid With Ring Topology

Sliding mode control can restrain the perturbations generated from the intermittence of the renewable energy generation and the randomness of local loads when microgrids are operating in islanded mode. However, the microgrid consists of several subsystems and the interactions among them will cause the chattering problems under the overall sliding mode control. In this paper, the chattering restraint issues for voltage control of the islanded microgrid with a ring topology structure are investigated based on the decentralized adaptive sliding mode control strategies. Firstly, we construct a tracking error system with interconnections considering the power transmission among subsystems and nominal values of system states. Secondly, we design linear matrix inequalities (LMIs) according to the H ∞ attenuation performance of the system external disturbances. Then, the tracking error performance and the control precision are guaranteed via the asymptotic stabilities of integral sliding mode surfaces. Adaptive laws are utilized to address the chattering problems of the sliding mode control. Finally, simulation results verify the effectiveness of the proposed decentralized control methods.


INTRODUCTION
Recently, there are abundant distributed generating devices permeating in the modern electric power systems for achieving the environment protection and the effective and flexible control of grids. In order to ensure the extensiveness and security of the power supply, microgrids have been the main form to transmit electricity to local loads for remote regions, which can operate in islanded mode or grid-connected mode (Mahmoud et al., 2014). Actually, an AC islanded microgrid consisting of distributed generation units (DGus) and energy storage devices can supply power to local loads steadily in low voltage magnitude (Kabalan et al., 2017). Because the microgrid contains numerous power electronic facilities, such as voltage source converters (VSC) et al., it is lack of immense inertia provided by rotating devices comparing with conventional grids (Zou et al., 2019). Furthermore, the renewable generation devices are usually affected by weather conditions and the power generated from them is usually intermittent and uncertain, so it is more complicated to realize the stable control of the multi-area microgrid voltage when it is in islanded mode (Zhou et al., 2021). At present, there are different control strategies to solve the voltage control problems of multi-area microgrids and optimize the control performance in islanded mode in order to improve the reliability and effectiveness of the power supply (Divshali et al., 2012;Sahoo et al., 2018).
The conventional control methods for multi-area microgrids operating in islanded mode demonstrate several disadvantages. The close-loop proportional-integral-derivative (PID) voltage control strategy can not estimate the errors between state variables and the nominal sinusoidal voltages accurately. Additionally, this control strategy presents bad control performance for restraining the inner parameter perturbations, such as frequency fluctuations (Vandoorn et al., 2013;Chen et al., 2015;Sefa et al., 2015). Zeb et al. (2019) combined the PID control method with fuzzy principles and designed the proportional resonant harmonic compensator as a current controller. Moreover, a phase lock loop (PLL) was designed to promote the speed of the system dynamic response. A comparison between fuzzy sliding mode control (FSMC) and fuzzy PID control illustrated that the dynamic response speed was lower and the tracking error performance was less precise via the fuzzy PID method. Considering that microgrids are sensitive about the system parameter variations, so the droop control technology is proposed to improve the robustness of microgrids via simulating the droop relationships among different electrical parameters (Avelar et al., 2012;Beerten and Belmans, 2013;Eren et al., 2015;Wang et al., 2019;Wang et al., 2021). Mi et al. (2019) modified traditional linear droop control strategies and utilized nonlinear droop relationships to describe the interactions between reactive power and voltages. The T-S fuzzy theory was applied to approximate the nonlinear model accurately and coordinate power among each DGu. Nevertheless, there were also errors between stable values and nominal values of voltages. Recently, sliding mode control (SMC) strategies are extensively applied in the stability control of microgrids for the superior asymptotic stability and robustness against parameter uncertainties (Hu et al., 2010;Karimi et al., 2010;Liu et al., 2017). An integration model of microgrids with complex meshed topology structures and several DGus was constructed to achieve the power sharing and voltage robust control (Cucuzzella et al., 2017;Wang et al., 2020). But the integration model could not represent actual interaction effects in different subsystems and the chattering was serious. Mi et al. (2020) proposed an adaptive sliding mode control strategy based on the sliding mode observer for wind-diesel power systems. The microgrid bus voltage showed remarkable stability via regulating the reactive power in terms of this method. Contrarily, the disturbance observer and adaptive algorithm brought in numerous parameters and promoted the complexity of the control system. To figure out the problem of harmonic disturbance in microgrids, Esparza et al. (2017) proposed a comprehensive control strategy to restrain the harmonic currents generated from DGus in AC microgrids. As shown in the simulation results, this strategy could cause the chattering phenomenon inherently.
Motivated by the aforementioned discussions, for the multiarea microgrid with a ring topology, the decentralized voltage control model will represent more appropriate relationships among the parameters in each local subsystem comparing with the integrated one. In addition, the adaptive sliding mode control (ASMC) strategy, which will be designed according to H ∞ attenuation performance of each subsystem, can ensure the robustness of the interconnected systems against mismatched uncertainties and external perturbations.
The main contributions of this paper can be summarized as follows: 1) The established multi-area microgrid model can depict the interactions among subsystems appropriately; 2) The reliability of solutions and the attenuation performance of external disturbances can be ensured based on the linear matrix inequalities (LMIs); 3) The proposed decentralized ASMC can restrain the chattering of the microgrid.
The rest of research includes four sections. Section Dynamical Models of Multi-Area Interconnected Microgrids constructs state functions with interconnections representing the topology structure of microgrid systems and defines tracking error models based on the nominal values of the state variables. Section Proposed Decentralized Adaptive Sliding Mode Voltage Controller introduces the designed decentralized voltage controllers in terms of the proposed ASMC theory. Section Simulation Results provides the simulation results and Section Conclusion illustrates the conclusion.

DYNAMICAL MODELS OF MULTI-AREA INTERCONNECTED MICROGRIDS
In order to explain the power transmission among the multi-area microgrid, the electrical three-phase diagram of the ring topology system composed four DGus is shown in Figure 1. The researched microgrid consists of local loads, power transmission lines and DGus. Because of various energy storage components in renewable generation systems, the DGus could be represented as DC voltage sources. The DGus connect with the points of common coupling (PCC) via VSCs and filters and provide power to local loads. PCCs can also link one of areas of the microgrids to another and connect microgrids with main grids.
Considering the ring topology structure of the microgrid and the power transmission orientations among different areas, the voltage control model of subsystem i with interconnections in the dq-coordinates in terms of Kirchhoff's Curent Law (KCL) and Kirchhoff's Voltage Law (KVL) can be obtained as follows, where N is the number of DGus in microgrids, L ti , C ti and R ti represent the inductance, capacitance and resistance of the filter connected with the DGu in subsystem i, respectively. The microgrid subsystems in various areas are integrated via interconnecting lines. L i and R i are the inductance and resistance of the interconnecting line between subsystem i and the adjacent subsystem. ξ ij is the orientation of the interconnecting line current between subsystem i and subsystem j (i ≠ j). ξ ij 1 and ξ ij −1 represent the current flows into and flows out the subsystem i. However, ξ ij 0 represents there is no power exchange between subsystem i and subsystem j. V di and V qi are the direct and quadrature components of the PCC voltage in subsystem i. I di and I qi are the direct and quadrature components of interconnecting line i. I tdi , I tqi , U di and U qi are the direct and quadrature components of the current and voltage generated from DGu in subsystem i. I ldi and I lqi are the direct and quadrature components of local loads. The randomness of the local loads and the power generation intermittence of DGus will cause frequency fluctuation in microgrids. Therefore, we introduce the parameter uncertainties and donate system frequency ω ω 0 + Δω. The matrix form of the dynamic (1)-(8) can be written as and F i ∈ R 6×2 are the system matrix, control input matrix and the external disturbance matrix of the ith voltage control model of the microgrid. ΔA i ∈ R 6×6 is a time-varying matrix representing the frequency fluctuation and E ij ∈ R 6×6 is the interconnection gain matrix consisting of ξ ij and the parameters of interconnecting line i. Assume that the nominal vector of the state vector in In view of (9), the corresponding error dynamic model in subsystem i can be expressed by For the later proof proceedings, we introduce the following lemmas, which can be needed to ensure the asymptotic stability of the system.
Lemma 1: (Mnasri and Gasmi, 2011) Consider the following unforced system: This system is regarded as quadratically stable and satisfies the H ∞ norm T yω ∞ < c. If there exists a quadratic Lyapunov function V(x) x T Px, with P > 0, then, for all t > 0, Lemma 2: (Mnasri and Gasmi, 2011) Let x and y be any vectors with appropriate dimensions. Then, for any scalar ϵ > 0, the following inequality holds: 2x T y ≤ ∈x T x + ∈ −1 y T Lemma 3: (Mnasri and Gasmi, 2011) Consider a partitioned symmetric matrix where A and C are square matrices with appropriate dimensions. Then, this matrix is negative define if and only if the matrix A and C − BA −1 B T are negative define.

PROPOSED DECENTRALIZED ADAPTIVE SLIDING MODE VOLTAGE CONTROLLER
The adaptive algorithm can optimize the parameters in controller and the decentralized strategy can improve the control performance. Design proceedings of sliding surface need to consider the stabilizing, tracking and restraining performance of the system. The sliding mode control law usually contains two parts, the switching control law and the equivalent control law. The former one can force the system state to approximate to the sliding surface when it deviates from the surface and the latter one can ensure the system state to keep on the sliding surface when it reaches on the surface. In order to design decentralized adaptive sliding mode voltage control laws for error dynamic model (11), the following assumptions are introduced. Assumption 1: All the parameter uncertainty matrices caused by frequency fluctuations are viewed as bounded. That means Assumption 2: For each subsystem i, For improving the dynamic response performance, we define the following integral sliding mode surface as where H i ∈ R 2×6 is a constant matrix satisfying H i B i is nonsingular and H i B i is positive for all i ∈ N. K i ∈ R 2×6 is the feedback matrix to be obtained via solving LMIs. Substituting Equation 11 into the derivative of sliding surface (15) yields (16) When the state trajectory of the tracking error system arrive and keep on the sliding mode surface, it would satisfy the following equation.
Based on Equation 17, equivalent control law can be represented as (18) Substituting Equation (18) into (11), the sliding mode dynamic equation can further be expressed as shows a more complicated tracking error system with parameter uncertainties and external disturbances. In the following procedures, we utilize the Lyapunov theory to analysis the system stability and the tracking performance to the nominal values of currents and voltages in each subsystem. Furthermore, we consider the H ∞ disturbance attenuation performance of interconnected system and design LMIs in terms of an H ∞ norm c i .
Theorem 1: Assume that the tracking error system (19) satisfies Assumption 1 and Assumption 2. If there exists a feasible solution X i > 0, and R i satisfies the following LMI (20), then we consider uncertain system (19) matches the H ∞ condition.
where Ω i X i A T i + A i X i − B i R i − R T i B T i + ε i I and ε i > 0 is a positive scalar. We consider the sliding mode surface is asymptotic stable. Proof: Select the following Lyapunov function for tracking error system (19).
Based on an H ∞ performance bound for the closed-loop system (19), one can obtain the following derivative.
If B i ≤ b i and Assumption one is satisfied, using Lemma 1, we get Equation 23 can be rewritten as The system under the equivalent control law is stable, if there is a feasible solution for the following LMI. Define E i (E i1 , /, E iN ), X i P −1 i , and R i K i X i . After premultiplying and post-multiplying (26) by diag[X i , I, /, I ], Equation 26 can be rewritten as where (20) is obtained with the method of Lemma three and the proof is completed.In the following section, we design the switching control in terms of adaptive algorithm to restrain the state chattering.
Theorem 2: Design the following controller (28) for closed-loop system (11) in terms of the feasible solution obtained via (20) and the system dynamic is asymptotic stable based on where q i1 and q i2 are positive parameters.
Proof: Let us consider the following Lyapunov function: where a i (t) a i − a i (t), and ρ i (t) ρ i − ρ i (t). Based on (28), (29) and (30), its derivative is given by Obviously, the derivative of the Lyapunov function V 2i (t) ≤ 0 is verified. That means the system states will reach the designed sliding mode surface in finite time for arbitrary s i (t) ≠ 0. Then, the proof is completed.

SIMULATION RESULTS
In this section, the proposed decentralized ASMC strategy is applied in the voltage control of microgrid with ring topology. The microgrid on study contains four DGus (N 4) and the nominal frequency is 60Hz, that means ω 0 120πrad/s. The electrical parameters of the subsystems and interconnecting lines are concluded in Table 1 and Table 2, respectively. The intermittence of the renewable generation and the uncertaintiy of the local load in microgrid will influence the power sharing among subsystems and cause frequency fluctuation indirectly. In this case, we consider the frequency fluctuation Δω sin(1000πt), the current generated by DGu in subsystem one is increased by 20% at t 1s and recover to the original state at t 2s. Furthermore, the current generated by DGu in subsystem three is reduced by 50% at t 1s and recover to the original state at t 2s. On the contrary, the operation states in subsystem two and four are constant. In order to ensure the power sharing, the voltages of PCCs and currents of interconnecting lines should also change. The reference values of voltages and currents in each subsystem are expressed in Table 3.
In the following simulation procedures, we analysis the simulation results and verify the validity of the proposed decentralized ASMC strategies under frequency disturbances and local load uncertainties. Because the system uncertainties are bounded, we can get a i ≥ 1, b i 1.7321. The initial states are In order to restrain the mismatched uncertainties and external disturbances, for tracking error system (11), the adaptive parameters are selected as q 11 1.2, q 21 0.9, q 31 1.1, q 41 1.5 Frontiers in Energy Research | www.frontiersin.org August 2021 | Volume 9 | Article 732997 The voltages and currents of the islanded microgrid demonstrate superior robustness and tracking error performance under the proposed decentralized ASMC strategy. The time evolutions of the dq-components of the currents generated from each DGu are depicted in Figure 2 and Figure 3 respectively in the case of load currents mutation. I ld1 increases 20 A at t 1s and I td1 increases 20 A synchronously, while I tq1 does not change significantly. Similarly, the current generated from DGu3 varies with the local load current in subsystem 3, and the current dynamic  The time evolutions of the dq-components of the PCC voltages of each subsystem are shown in Figure 4 and Figure 5. Considering the load current variations in the interconnected microgrid system, V d1 is decreased by 5 V and V d3 is increased by 5 V. Meanwhile, I d1 provided by subsystem one is reduced and I d3 provided to subsystem four is improved. Then, the power sharing among each subsystem can be ensured. As shown in Figure 4, there exist deviations between initial voltage values and nominal values, but the system voltages can also track to the nominal values and maintain stable. When the d-components of the  voltages change in small scales, the q-components of the voltages fluctuate and remain stable in a short time.
The time evolutions of the dq-components of the currents of interconnecting lines are represented in Figure 6 and Figure 7. Under the influence of mutations of load currents and PCC voltages, the currents of interconnecting lines are only influenced by the voltages of PCCs and do not deviate from the reference values appreciably, which illustrates the remarkable robustness of proposed ASMC strategy against the external disturbances and mismatched uncertainties. That also means the changes of local  August 2021 | Volume 9 | Article 732997 load currents will not influence the stability of the general microgrid. Notably, the current orientation of line four is opposite compared with the currents of other lines because the voltage of PCC four is lower than that of PCC1. Figure 8 and Figure 9 depict the three-phase waveforms of currents generated from DGus. Figure 10 and Figure 11 depict the three-phase waveforms of voltages of PCCs in subsystem one and subsystem 3. In islanded mode, the decentralized controllers are  August 2021 | Volume 9 | Article 732997 11 mainly designed to standardize the voltage and current waves and improve the power quality of AC microgrid. In Figure 8 and Figure 9, the amplitude of three-phase wave of the current generated from DGu1 increases 20 A and that of DGu3 decreases 20 A at t 1s, which matches with the variations of load currents. In Figure 10 and Figure 11, it is obvious that the three-phase waves of the voltages of PCC1 and PCC3 maintain in standard waveform and the effectiveness and reliability can be proved adequately.

CONCLUSION
In this paper, the chattering restraint issues for voltage control of the islanded microgrid with a ring topology structure have been solved via decentralized adaptive sliding mode control strategies. The constructed tracking error system with interconnections has depicted the interaction among each subsystem appropriately. The control matrices in sliding mode surfaces have been obtained via solving the LMIs, which combine the H ∞ attenuation performance of the system external disturbances with the asymptotic stabilities of integral sliding mode surfaces. The controller parameters have been optimized by means of adaptive algorithms. The simulation results have illustrated the effectiveness of the proposed decentralized ASMC strategies. In future, further research will be extended to the nonlinear and time-delay system.

DATA AVAILABILITY STATEMENT
The raw data supporting the conclusions of this article will be made available by the authors, without undue reservation.