{'fraction_non_alphanumeric': 0.01510989010989011, 'fraction_numerical': 0.0, 'mean_word_length': 5.813084112149533, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 0, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
A tutorial on ferroresonance

Ferroresonance is a widely studied phenomenon but it is still not well understood because of its complex behavior. It is “fuzzy-resonance.” A simple graphical approach using fundamental frequency phasors has been presented to elevate the readers understanding. Its occurrence and how it appears is extremely sensitive to the transformer characteristics, system parameters, transient voltages and initial conditions. More efficient transformer core material has lead to its increased occurrence and it has considerable effects on system apparatus and protection. Power system engineers should strive to recognize potential ferroresonant configurations and design solutions to prevent its occurrence.