{'fraction_non_alphanumeric': 0.029382957884427033, 'fraction_numerical': 0.04407443682664055, 'mean_word_length': 5.047337278106509, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 1, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
Analysis of lightning surge propagation in wind farm

Wind power generation is expected to become more important in future distribution systems. Although several prospective reports such as IEC 61400‐24 and NREL SR‐500‐31115 indicate an insulation scheme and grounding design for lighting protection, there still seems to be too few investigations on the problems. This paper therefore discusses lightning surge analysis using a wind farm model with 2 or 10 ideal wind turbines. Changing parameters such as grounding resistance and lightning strike points, several cases were studied. As a result of the analysis using digital simulator ARENE, it is clear that the surge tends to propagate toward the end of a distribution line in a wind farm and there is the possibility of insulation accidents at the other wind turbines when lightning attacks a wind turbine. © 2007 Wiley Periodicals, Inc. Electr Eng Jpn, 162(2): 30– 38, 2008; Published online in Wiley InterScience (www.interscience.wiley.com). DOI 10.1002/eej.20364