{'fraction_non_alphanumeric': 0.019882179675994108, 'fraction_numerical': 0.004418262150220913, 'mean_word_length': 4.782978723404256, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 0, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
Quieting Weinberg 5C: a case study in hospital noise control.

Weinberg 5C of Johns Hopkins Hospital is a very noisy hematological cancer unit in a relatively new building of a large medical campus. Because of the requirements for dealing with immuno-suppressed patients, options for introducing sound absorbing materials are limited. In this article, a case study of noise control in a hospital, the sound environment in the unit before treatment is described, the chosen noise control approach of adding custom-made sound absorbing panels is presented, and the impact of the noise control installation is discussed. The treatment of Weinberg 5C involved creating sound absorbing panels of 2-in.-thick fiberglass wrapped in an anti-bacterial fabric. Wallpaper paste was used to hold the fabric to the backing of the fiberglass. Installation of these panels on the ceiling and high on corridor walls had a dramatic effect. The noise on the unit (as measured by the equivalent sound pressure level) was immediately reduced by 5 dB(A) and the reverberation time dropped by a factor of over 2. Further, this drop in background noise and reverberation time understates the dramatic impact of the change. Surveys of staff and patients before and after the treatment indicated a change from viewing the unit as very noisy to a view of the unit as relatively quiet.