{'fraction_non_alphanumeric': 0.019801980198019802, 'fraction_numerical': 0.01782178217821782, 'mean_word_length': 5.246913580246914, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 0, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
Research on Large DC-Biased Power Transformer

A 3D transient eddy current field analytical method is presented to calculate the additional loss and temperature rising in three-phase banks with separate single-phase transformers under DC biasing current. A SF-31500/110 double-winding transformer connected in two-phase exciting mode is applied to test the calculated data, and countermeasures against DC bias are proposed based on the discussion of influences on the excitation current and magnetic flux.