{'fraction_non_alphanumeric': 0.006686930091185411, 'fraction_numerical': 0.0, 'mean_word_length': 5.0962962962962965, 'pattern_counts': {'":': 0, '<': 0, '<?xml version=': 0, '>': 0, 'https://': 0, 'lorem ipsum': 0, 'www.': 0, 'xml': 0}, 'pii_count': 0, 'substrings_counts': 0, 'word_list_counts': {'cursed_substrings.json': 0, 'profanity_word_list.json': 0, 'sexual_word_list.json': 0, 'zh_pornsignals.json': 0}}
FEATURES OF LIQUID FLOW DISTRIBUTION IN PLATE HEAT EXCHANGERS REFERENCES

The relevance of the work of information and diagnostic systems in the field of monitoring of plate heat exchange equipment is considered. The reliability of the monitoring devices requires an accurate mathematical description of the thermo hydrodynamic processes in the heat exchange channels. The classical description of these processes implies a uniform distribution of the flow rate of the working medium along the length of the plate package, which in turn implies equal conditions for the formation of salt deposition products on the heating surfaces of the plate heat exchanger. The use of dependencies that take into account the equality of costs for a package of plates reduces the reliability of diagnostics of the efficiency of hot water devices of the plate type. Since the geometric space formed by the plates is represented by parallel channels connected by sections of transit collectors, the method of resistance characteristics is proposed as a method of hydraulic calculation of the distribution features of liquid flows through heat exchange channels. The dependence of the design features of the location of the interplate channels relative to the input of the coolant into the distribution manifold is revealed. It is found that, the flow rate of the circulating coolant is less in the channels most remote from the inlet pipe than in the nearest channels. The hypothesis of the influence of the relative position of the channels in relation to the inlet pipe is confirmed by numerical studies of the hydrodynamic regime of the plate heat exchanger.