110 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works   Auto   Thermal Faults   Safety switch   Moment fault   End limit switch low   End limit switch high   Emergency stop  The fault inputs will make the object go into fault. The actual fault will be indicated on the SCADA  system until the object is reset or as long as the fault is active.  Start counters is handled by the object  8.23.10 Standard regulator (Controller)  A standard regulator shall as a minimum be provided with the following functions and parameters:  Set point for regulator  The status-handling object is a standard routine handling individual status/alarm inputs and command  outputs. (Level switches etc.) or communication  Running in of all regulators shall be carried out by the Contractor.  All input can by means of the option word individually be configured to be status or alarm.  Status inputs will be indicated in the status word as long as the input is activated. Alarm inputs will make the object go into fault. The actual fault will be indicated in the status word  until the object is reset or as long as the input is active  The system alarm handling object is a standard routine handling specific system alarms generated by CMS s and communication units.  The following alarms shall be generated and displayed at the CMS system.  8.23.12 System alarm  8.23.11 Status/alarm handling 1  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc   Cycles time limit exceeded   Battery exhausted or missing   I/O error with diagnostics   Manual adjusting by operator of regulator output (regulator in manual).  Manual adjusting by operator of set point   Limitation of regulator output, low and high   Calculation set-point, low and high (option)   PID-regulator with adjustable parameters. The I-time shall be adjustable from 5 sec. to 5 min.  Status of the regulator : Auto, Local, Manual 