109 of 124  A global function shall prevent more objects to start at the same time. The fault inputs will make the object go into fault. The actual fault will be indicated on the SCADA  system until the object is reset or as long as the fault is active.  The object supervises that a running signal is coming within a specific time after a start command has  been given. If the running signal is not present before the time has elapsed the object will go into fault  and the supervision fault will be indicated. The function works both ways, i.e. if the running signal is  present when the start command is zero.  Hours and start counters is handled by the object  The valve routine object is a standard routine handling a mono-stable motorvalve control.  The object can be in 3 different modes:  It handles the following input signals or communication:  8.23.8 Motor valve routine 1  8.23.9 Motor valve routine 1-1  The fault inputs will make the object go into fault. The actual fault will be indicated on the SCADA  system until the object is reset or as long as the fault is active.  The object gives alarm if a maximum time for opening or closing is exceeded.  Start counters is handled by the object  The valve routine object is a standard routine for supervision only.  The object can be in 2 different modes:  It handles the following input signals:   Auto   Manual (from local panel)   Auto   Operator (from operator station)   Manual (from local panel)   Auto   Thermal Faults   Safety switch   Emergency stop   End limit switch high   End limit switch low   Moment fault   It handles the following output:   Start contactor open   Start contactor close  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works 