108 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works  Hours and start counters is handled by the object.  The object is a standard motor routine handling motors with no command outputs (Motors controlled  by local machine installations). The object can be in 2 different modes:  8.23.6 Motor routine 1-1   Auto   Manual (from local panel)   Auto   Thermal Faults  It handles the following input signals or communication:   Moisture faults (if available)   Safety switch   Emergency stop   Actual current (motors with frequency and soft starter)  The fault inputs will make the object go into fault. The actual fault will be indicated on the SCADA  system until the object is reset or as long as the fault is active.  Hours and start counters is handled by the object.  The object can be in 3 different modes:  The object is a standard motor routine handling motors with two directions or two speeds.  8.23.7 Motor routine 2   Auto   Operator (from operator station)   Manual (from local panel)   Auto   Thermal Faults   Moisture faults (if available)   Safety switch   Emergency stop   It handles the following output:   Start contactor 1   Start contactor 2   Actual current (motors with frequency and soft starter)  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc  It handles the following input signals: 