10 of 74  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 3: Plant Description   At the effluent outlet.  Sampling of wastewater and treated effluent at the various locations listed above shall be carried out  with automatic (flow proportional and time controlled) composite sampling units. The samples shall  be refrigerated. The complete sampling equipment shall be included in the Contract. In relation to the current legislation, “Real Time Remote Monitoring Station” at the outlet of  wastewater treatment plants shall also be supplied and installed by the Contractor within this Contract.  Relevant permits, applications, official and administrative correspondences shall be carried out by the  End Recipient.  The Contractor shall ensure that all sampling points in the wastewater treatment plant have an open  section with suitable safe access to allow the taking of grab samples.  Sampling points for grab samples shall be provided at appropriate places in the sludge pumping and  dewatering installations.  3.2.5 Laboratory and analytical equipment  As a minimum, the laboratory equipment shall include:  The Contractor shall provide laboratory facilities for the analysis of the wastewater. The laboratory  shall be equipped with analytical instruments, furnishings and equipment necessary for carrying out  the testing of wastewater and sludge samples taken at the plant. The laboratory shall, as a minimum,  be capable of carrying out testing of suspended solids, total solids, determination of SVI and  microscopic assessments for sludge, COD, BOD$_{5}$, ammonia-N, nitrate-N, total-N, Ortho-P, total-P,  pH, temperature, dissolved oxygen, alkalinity and volatile fatty acids (VFA).   Emergency Shower With Eyes-Washing   Oxitop 12 Bottles   5 pc. Imhoff Vessel with Support   Bacteria Incubator   Two sets of BOD Incubator  Working range 20 (+/- 1) °C  Microprocessor controlled  Minimum volume 120 litres   Drying Oven  Microprocessor controlled  Heating range 50-250 °C (+/- 1)  Minimum volume 120 litres  Ash Muffle Furnace  Microprocessor controlled  3_Vol3_d4.3_Section 3_Plant Description_GIR_rev08 