100 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works   The last line shall include the accumulated value for the period of the report for the data  collections.   The periods shall be of 1 hour each. The hour-mean value shall be included for each hour.   The daily mean shall be included in the second last line.   All measurements and parameters shall be included in the report.   The accumulated value for sum up values (water quantities etc.) at the time the report ends  shall be included in the last line.   The daily report shall automatically be printed.   The periods shall be of 24 hours each. The daily mean value shall be included.   The monthly mean value shall be included in the second last line.   All measurements and parameters shall be included in the report.   The accumulated values for measurements at the time the report ends shall be included in the  last line.   The periods shall be of 1 month each. The monthly mean value shall be included.   The yearly mean value shall be included in the second last line.   All measurements and parameters shall be included in the report.   The report shall automatically be printed the 1st of January.  The accumulated values for measurements and parameters at the time the report ends shall be  included in the report.   The alarm report shall be printed at the operator's request. It shall be possible to select start  and stop time for the period of report.   Automatic printing of the report shall at a defined time be possible.   Component no.   Alarm text (min. 25 characters)  Time for start of the alarm   Time for acknowledge of the alarm   Time for stop of the alarm   Alarm priority   Name of person that acknowledged the alarm   The actual alarm value  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc  The report shall as a minimum include the following information:  Daily Reports:  Monthly Reports: Alarm Report:  Yearly Reports: 