Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works   Check if the program can start up normally.  Perform a normal removal of program.  Make a subsequent reinstallation. 115 of 124   No errors occur during the installation procedure.   The procedure is in accordance with the instructions.   The program is able to start up normally.  The criteria for passing the final test will be:  The purpose of the test of the normal operation of the SCADA system is to make sure that it is  possible  to  operate  the  program  in  a  logical  way  and  in  accordance  with  the  specifications/documentation/O&M Manual.  During the test of the normal user operation, the test operator shall:  8.24.7 Normal Operation   Guide him-/herself through a large number of menus and dialog boxes and test a large number of  various commands.   Print different kinds of reports.   Every activity of normal operation leads to the expected result, and activating a command leads  to the expected dialog box.   A printing command leads to printing of the correct output.  The criteria for passing the final test will be:  The purpose of this test is to verify correct and logical handling of errors.  The test operator shall:  Handling of errors:   Provoke a number of errors and verify that the system responds to these errors as described in the  requirements.  Report any unexpected error during all tests in order to verify robustness.  The criteria for passing the final test will be:   Indications of errors must be reasonable, and the user shall be able to continue the work on a  well-defined basis.  Handling of Help functions:  The purpose of the test of the handling of help functions (on-line or in manual) is to make sure that the  on-screen help function is adequate and works in accordance with the requirements and the actual  program. In particular, it shall be verified that terms are used consistently.  The operator shall perform the following tests:   The help system shall be consulted a large number of times in different situations. The operator  shall focus on the existence of relevant help, on clear language, on relevant link(s) to more help  and on consistent use of terms.  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc 