Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works  91 of 124  instant view(real time) data and historical data in ruler format and alarm history in list format into  database  Record configuration will be made by mark and click format and it will not require any code writing.  Target database will be full licensed database version and will provid all normal data cess, data  changing and reporting options for end user. Operator interface will maintain interface for getting fata from Active X Data Objects(ADO) Data  sources(SQL Server, Oracle,etc). Receiving data, long term query and slow connection will work  asynchronously such that it will not effect other Operator interface functions. Access will be provided for ADO data as connected or disconnected data set. It will have integration with MS Office Excel which is suitable for access and reporting without  requiring programming. It will have record system which is installed over MS SQL Server 2008 R2 platform. It will be structure which is open to integration with ERP and MES system. Record system will collect data from redundant Operator Interface Server structure. It will continue to  record data over redundant server in server failures. In the event that server connections are  disconnected completely, data which were buffered and coult not be retrieved in real time will be  transferred to record system with respect to time values when connection is established with server  system again. Record system will be able to make record at 100 ms or slower speeds Deadband filtering will be able to be made baed on data for data to be recorded in record systems. Record system will have ability to make archiving for at least 100 tags. Record system should be open to different report and data access without making any change in client  structure and operator interface. Record system should be suitable with Microsoft Reporting Services, MS Office Excell Add In  Support and reporting to be prepared in this medium. Also access should be maintained for data which  is recorded bt web client structure from different locations within enterprise. Operator Panel (HMI)   There will be operator panels with minimum 10 inch screen size indicating all analog and  digital data including color scheme for group for monitoring stations where they are connected  with. They will be placed over control boards.  Operator panels should have UL 508, CSA C22.2 (#142), UL1604, ANSI/ISA 12.12.01, CSA  C22.2 (#213) certificates   TCP/IP communication should be maintained as standard.  Operator panel software should support Microsoft Windows 7 64 bit version.  Alarms which occur in system should be able to stored in memory and printout should be able  to be taken from printer when required.  Different functions should be able to be created by writing code by HMI software.  Screen will have QVGA resolution and will have minimum 65000 color capacity. 8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc 