Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements Section 09: Building Works  13 of 24  Locks:  1. Tabular cylinder locks: stainless finish  2. Entry, exit and office doors: keyed on side, button opposite side   Passage doors: knobs both side, no lock   Storage room: single knob with key   Toilet room: stainless outside, chrome inside, pin opening outside for emergency with button in- side   All keyed locks to be master keys for same building   All locks to have two key each   Door closers: heavy duty type with stainless cover; top installation for either right or left hands  operation   Stops: floor or wall mounted type, stainless   Door pull: 10 x 30 cm stainless plate, with 15 cm shaped pull securely fastened to plate; mounted  with oval head stainless screws.   Kick plates: 20 cm stainless plate, width of door less 5 cm   Coat holder: stainless steel, standard   Door hinges: 10 x 10 cm stainless steel, three per door   Flush bolts: 15 cm stainless   Gravity hinges: set of upper and lower, chrome finish, adjustable to stay slightly ajar   Cabinet hinges: 6 x 10 cm stainless, three per door   Friction catch: heavy duty - two parts with rubber grips concealed installation   Cabinet and drawer pulls: stainless steel, 10 cm grip with concealed bolt fastenings   Window hardware:  Windows indicated to be pivot type shall be furnished with a pair of window fittings (friction stays), a  window pull and one barrel bolt lock. Window fittings shall be galvanised or stainless steel. Window  pull shall be 2.5 x 10 cm with 4 screws and barrel bolts 10 cm long, 6 mm bolt.  Unless otherwise indicated, all hardware installation and hanging shall be done at the site.  Exteriors doors and doors in air conditioned areas shall be weather-stripped.  Provide one (1) painted wood key case in each structure, size 25 x 50 cm with door and lock. Supply  plywood back inside with hooks for spare keys. All keys shall be clearly labelled with metal or hard- board tags size approximately 50 x 20 securely fixed to the keys and handed over to the Engineer.  Upon completion of the hardware installation, all items shall be inspected for proper operation. All  work shall be protected and any damage or incorrectness shall be repaired.  Hardware shall not be fitted until the latest time in the Contract.  9_Vol3_d4.3_Section 9 building works_en_GIR_rev6.docx 