99 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works  It shall be possible to select the parameters for data collection and the time interval for the data  collection.  In addition it shall be possible to key in data manually. The manual keyed in data shall be included in  the data collection program and be part of the reports.  A program for calculation shall be included. It shall include all common arithmetic functions.  The program for calculation shall have access to all elements, name, parameters and data in the  system. It shall be possible to include time marking of the calculation program in order to control the  calculations after a calendar program.  Programming of the calculations shall be in a high level language. 8.22.2 Data Presentation  Reports and Lists:  The format of reports for indication on the monitor and for printing shall be generated from data base  programs. It shall be possible to select the data to be indicated on the monitor or printed from menu  commands that automatically will start the report in question. It shall be possible to print reports  automatically.  It shall be possible to select the following reports from the menu:   Alarm report   Event list   Daily report   Monthly report   Yearly report.  The data base program shall include the possibility of configuration and editing the format of the  reports.  Format and lay-out of all reports shall be approved by the Engineer.  General Lay-out of Reports:   Date and time for printing of the reports shall be indicated.   The period the report covers shall be indicated.   In column no. 0 the period shall be indicated.   Data shall be indicated in column no. 1 and onwards. A minimum of 8 characters shall be  included in each line.   In line 3 the unity shall be indicated.   In line 1 and 2 the name and component number shall be indicated (space for 16 characters).   In the following lines the measured value or calculated value shall be indicated for the data.   The second last line shall include the mean value for the period of the report.  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc 