67 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works  4 meter CCTV camera poles will be used in areas which are not suitable for installing illumination  poles in WWTP. There will be PoE supporting equipments for camera system. Properties of PoE equipments  Interface  5 x 10/100Mbps RJ45 Port  Network connection  10BASE-T: UTP category 3, 4, 5 cable (maximum 100m) EIA/TIA-568 100Ω STP (maximum 100m)  100BASE-TX: UTP kategori 5, 5e cable (maximum100m)  EIA/TIA-568 100Ω STP (mximum 100m)  1000BASE-T: UTP category 5, 5e, 6 or more cable (maximum 100m) EIA/TIA-568 100Ω STP (maximum 100m)  PoE Ports(RJ45)  Standard: 802.3 af compatible PoE Ports4 Port PoE  Power supply: 60W  External power supply  220v  Certificate  FCC, CE  8.17.2 Fire Fighting System  The system shall be installed in accordance with the latest issue of “Turkish Regulations for Fire  Protection in the Buildings” published in the official journal dated 26 July 2002 and numbered 24827  and international standards. All materials to be offered shall be manufactured in accordance with at  least one of CE, EN, DIN, VDE, and etc. standards and shall have certificates obtained from at least  one of UL or FM international approval foundations. The manufacturer company shall have ISO  quality certificates.  Analogue Addressed Fire Alarm Network; The control panel shall be modular and have the number of zones as indicated. It shall be 2-cycled  with 24 zones, have analogue addressed fire alarm network addressing capability and 24 fire zone  indicators. The analogue addressed fire alarm network shall be compatible with addressable smoke,  heat, gas and temperature detectors, addressable internal and external type fire alarm buttons, input  and output interface units, short circuit isolators and connections of addressable audible alarm devices.  The network shall be manufactured with microprocessor technology and its capacity shall contain 1, 2  or 4 cycles. At least 127 addressable devices should be connectable to each cycle. The fire alarm  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc  RACK TYPE NAS STORAGE UNIT Type :NAS Storage  Capacity:24 TB 2 x 10/100/1000 Base-TX (Gigabit Ethernet) One (1) USB 2.0 (front) Two (2) USB 2.0 (rear)  One (1) VGA (rear)  one(1) PS/2 keyboard(rear)  one (1) PS/2 mouse (rear)  Male DE-9 serial (rear)  8 x 3 TB 3,5” NAS storage, Sata 3 (6 gb/s) 200MB/s reads and writes  2 x 250 Watt 100 V– 240 V AC , Redundant hot-swap PSU