62 of 74  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  3_Vol3_d4.3_Section 3_Plant Description_GIR_rev08  The tenderer shall provide with the detailed electrical consumption table similar to the one below. For  all consumer items in the list, the tenderer shall provide calculation/supplier’s data and explanations.  The tenderer shall follow strictly all the conditions herein stated in his power calculation for hydraulic  load. Any other assumptions, figures and factors shall NOT be used unless clearly stated. The flow through the Works which shall be used to calculate the annual Hydraulic Load dependent  power consumption is the average yearly flow as derived Volume 3 Section 2 Design Basis (Section  2.2) for Stage 1 – 2032.  The unit rates for hydraulic load shall be provided for 25%, 50%, 75% and 100% flow of the average  yearly flows as derived. The Tenderer commits that hydraulic load (wastewater volume) dependent power consumption for the  Inlet and Intermediary Pumping (if any), preliminary and primary treatment and those components not  included in (b) or (c) is less or equal to the one declared in Volume 4 Schedule 11.1. The committed consumption of power as supplied to the Plant is based on hydraulic load, organic load  and sludge load.  The commitment for power consumption is provided as the yearly maximum consumption, excluding  consumption for building services and heating.  The Tenderer hereby commits that the consumption of power is less or equal to the specified below:  For yearly electrical and chemical consumption calculations, 365 days shall be taken into  consideration for one year.  At the end of the year, all the actual unit rates shall be available to the Engineer. According to the  actual flow/load (in pro rata to the average conditions as stated above), the Tenderer’s committed  figure for each item shall be determined. To perform this, a scatter type graph (unit rate against  flow/load for the four data set for 25%, 50%, 75% and 100% flow/load case) shall be plotted for the  Tenderer’s committed figures and a trend line (polynomial, logarithmic or else whichever suits to the  Tenderer’s data) shall be applied. Therefore an equation (F(x)) shall be developed. The actual  flow/load figure shall be accounted for “x” in the equation and unit rate based on this “x” value shall  be calculated with the help of equation (e.g. if the actual flow rate measured is 60% of the Stage 1  average flow rate, then “x” shall be 0.60 and Tenderer’s committed figure shall be calculated with the  help of equation. If this correlated unit rate is NOT less or equal to the actual unit rate, then the  penalties shall be paid to the End Recipient by the Contractor as described in the following sections.  values shall be measured, shall not be in the same compartments, each group shall be present in  separate board compartments.  3.4.1 Electric Power Consumption Commitments  3.4.1.1 “Hydraulic Load” derived commitment for the plant components:  Conditions 