Europol Public Information For currently 57 Remote Sites (EU Member States, Non EU States and 3 rd  Parties) (MS/NEUS/3rd Parties)  worldwide a special Paramount rack and infrastructure was developed.  The black Paramount 42U rack (h*w*d = 42RU*600*1000) has been split into 2 compartments. The upper  part (36RU) is a secure part where Europol components are mounted. The lower part (6RU) is used for  the telecom provider who has free access to this compartment. Because of the height a special  Schleifenbauer switched and metered 16A PDU is supplied with a black cable for the A-feed and a grey  cable for the B-feed. The lower telecom compartment also has a small PDU (A and B feed) for its own  power needs. Through the DC Spyder management tool the PDU’s can be remotely managed. Each rack is  labelled at both front and back with label <country>-<city>-<rack> and label that warns to contact  Europol ICT Operations team first before opening.  A special camera stand with two cameras mounted on top of the rack gives the Europol ICT Operations  team in Europol HQ the possibility to remotely monitor the person in front or to the rear of the racks as  well as view any work inside of the rack. The MS/NEUS/3rd Parties racks are equipped with in total 100  fixed dome camera’s, all connected via the private Europol network to 3x 32 channel NVR servers and 1x  16 channel NVR server located at Europol HQ. All video streams are stored at the Europol HQ site and can  be viewed by Europol ICT staff via a remote client connection with the WinPak system.  The MS/NEUS/3rd Parties racks count a total of 57 single racks equipped with 2 slide handle locks and  several contacts and alarms connected to an intelligent controller in the same rack. These Intelligent  Controllers are all connected via the private Europol network to the Winpak Server at HQ. A local client to  the WinPak system at Europol HQ is used to operate and monitor these doors and alarms.  The slide handle locks on front and rear side of the racks can only be opened based on a command from  the Europol ICT staff operator. A keypad is mounted on the front side of the rack to be able to open the  doors in case of emergency.  For standardization purposes the same cabling, rack, PDU, security and monitoring concepts are used as  in the DR Sites.  Additional Remote Sites are added, where black Grate Lake 24RU racks (h*w*d = 24RU*600*800) are  placed with all security controls mentioned above except the split compartments and the cameras.  In Europol JWF13, 1 Satellite Equipment Rooms (SERs) is situated.  It has SER with 4 racks (h*w*d = 41U 2000mmx 800mm x 1000mm). Each rack is labelled in both the  front and back with label JWF13-<row>-<rack>.  Each rack is equipped with 2 switched and metered PDUs, single phase 32Amp with 18 x C13 sockets and  6 x C19 sockets each. The PDUs are positioned on the rear left and right side of the rack. All racks have an Automatic Transfer Switch (ATS) with 1 x C20 IN and 8 x C13 and 1 x C19 OUT. This is  combined with a 19” rackmount PDU with 8x Schuko connections.   Page 12 of 35  7.3.4. Europol Satellite Building JWF13