Europol Public Information Compose Click ‘n Go structured cabling is used in all racks. Based on this concept, a mix of copper and  fibre modules is provided on a small amount of Rack Units (RU’s). Type of fibre cable: OM3 Multimode  Fibre 50/125μ; Type of fibre connector: LC female;  Type of copper connection: S/FTP round CAT 6A; Type  of copper connector: RJ45 female.  The racks in the SER in Europol Second Satellite Building (ESB) are expected to be similar to the racks as  described in the Europol Satellite Building JWF13.  Europol is looking at building a second site with office space and a data centre. The alternative location  can be built anywhere in EU, but for this tender, Europol considers the alternative location to be built in  Somewhere in The Netherlands (SNL).  The description below gives the tenderer a reasonable understanding of the work to be carried out if  Europol decides to approve the plans for an alternative location. The tenderer will use it to prepare its  Technical offer.  For this tender, please assume that Europol will build the SNL in an existing building within 100km of  Europol Headquarters, The Hague. The SNL consists of the following areas:  SNL Data Centre will be built in a large open space with concrete floor, the height is 3.5 meter. Europol is  allocated the required surface in one corner. Europol wants to implement 10 rows of 5 racks starting at  the short wall. Via the roof of the rack, one rack (the network rack) will be used to interconnect with the  remaining racks using 24 fibre pair and 24 copper pair. In this rack also the telecom provider  infrastructure is located being two rack unit patch panel. Space for 5-10 racks is available for external  provided racks delivering services to Europol. This space is separated from the Europol racks by a  wall/cage wire and has its own entrance independent from the entrance to the Europol racks.  The SNL Data Centre needs to be secured including door controls and camera controls. Each rack will be  equipped with 2 switched and metered PDUs 3 phase 32Amp PDU’s with expected consumption of  7000Watt per rack. The central power distribution switch is available but need to be expanded to each  rack. Raised floor and hot or cold aisle needs to be created under this contract and needs to be flexible  for expansion. It might be that the raised floor, cooling and automatic fire extinguisher will be provided  by the Host State as part of the agreement but it might as well that this needs to be provided under this  contract. The floor space for 5-10 racks won’t need hot/cold aisles.   Page 13 of 35   SNL Data Centre  • SNL Office space for 50 staff  • SNL Data Centre  7.3.5.2. Creation of a new Data Centre and Office Space (SNL)  7.3.5.1. Creation of a new Data Centre and Office Space in ESB  7.3.5. Creation of new Data Centres and Office Space (ESB and SNL) 