114 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works  Miscellaneous  After installation on site  8.24.4 Automation  8.24.5 Usability  8.24.6 Installation and start up  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc  The test shall:  The purpose of this test is to make sure that the installation and start-up procedure functions well and  is described correctly in the Operation and Maintenance Manual.  Perform an installation procedure in accordance with the O&M Manual.  Check if the procedure is in accordance with instructions. This part describes the tasks to be performed to test the usability of the program. Below, each issue is described. At the end of each item, a number of criteria for passing test are  described.   The automation system covers the CMS system.  The test shall cover a number of different issues:   Usability (general operation of the automation and CMS system).   Efficiency (performance).   Accuracy (correct handling of values and calculations).   Security (protection against unauthorised use of the CMS system).   Flexibility (verification that the automation system is suitable for upgrading).   Control of inside temperatures under max. load.  Control by use of thermal photographing under max. load  Control of component layout in accordance with the documentation   Control of front layout   Control of handles and locks   Control of drawings in panel   Control of cleaning   Control of sufficient spare capacity and room   Control of covered race trays   Control of earth system   Control of panel marks and certificates   Control of labelling   Control of section covers 