123 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works   Start-up, operation, and shutdown instructions for system. These shall include process control,  hydraulic control, power, and auxiliary systems;   Procedures to deal with breakdown and emergencies;   Safety requirements;   Full maintenance instructions for all equipment including planned maintenance schedules or charts  giving daily, weekly, monthly, quarterly, half yearly, annually and overhaul instructions, together  with recommended lubricants and spares. These should also include details of routine maintenance  work that shall be within the competence of the normal maintenance staff, and notification of  maintenance work that shall done by the manufacturer, his agent or other specialist operator;   Step by step procedure for the dismantling, repair and re-assembly of all items of equipment  which shall be complemented by photographs and exploded diagrams;   Fault finding charts;   Certified suppliers drawings of all equipment supplied, which are to be scheduled for easy  reference;   Site test reports for all electrical, electronic, mechanical and water systems. Site test process  reports for proving tests, commissioning reports, and suppliers test certificates;   Copies of performance curves;  List of settings of all parameters for Plant automation and control at the time of handing over the  Works to the End Recipient.  Four (4) copies of each set of manuals, in English and Turkish shall be submitted to the Engineer  before taking over. The manual shall be submitted to the Engineer both soft copies and hardcopies.  Each volume shall be durable and permanently bound within a stiff binder of a design to be approved  by the Engineer. They must each permit the subsequent incorporation of revisions to be necessary  during the Defects Liability Period. The Contractor shall provide in addition to the above a complete set of the operating and maintenance  manuals on the corresponding computer files (AutoCAD, MS Office, etc.) on CD’s [4 sets].  All drawings, unless within word-processing documents, shall also be provided in AutoCAD format  on disk, or other media agreed with the Engineer. All documentation shall conform to ISO 6592 Code  of Practice for Documentation of Computer Based Systems. The documentation must be designed  such that the system design and function are clear and easy to recognize, and that optimum  maintenance and repair are guaranteed. 8.26.2.1 Hardware Layout Drawings  8.26.2 Documentation in respect of the Control Centre  8.26.2.2 Source Code  These shall consist of schematic drawing indicating computer hardware to be present in the control  centre, the peripherals, display systems, etc. Important technical features belonging to all parts to be  included in this diagram shall also be provided in list format.  This shall consist of a documentation showing all source codes of the programs to be written  according to instructions of the Engineer for the applications that cannot be performed by the standard  functions of the SCADA software, and a copy of the source code created in a digital medium.  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc 