90 of 124  Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 8: Electrical Works  to other by using standard tools without requiring any information regarding with operator interface  software. There will not be limit in number of languages which can be change while system is running. Installation for only runtime mode  Multiple monitor mode  It should be able to install software such that it will run without integrated development components.  Software should run in runtime environment for viewing graphical page, real time data. Tools which  will organize configuration will not be used in installation.  Graphical system will support multiple monitor layout.  1x4   2x2   4x1  End user will be able to configure which graphical page will be viewed in start up in each monitor. Firstly any software, special code will not be required for standard functions such as back up, reload  and adding historical data. There will be integrated high level language which is designed particularly  for operator interface applications and it will have multiple task and preventive properties. Besides  there will be documentation language in language which is compatible with VB. High Level Languages  Document Online Modifications  Database Integration  Video Integration  8_Vol3_d4.3_Section 8 electrical works_en_GIR.rev8.doc  Operator interface software or integrated package wil be able to store important Operator Interface  Data to Associative database including MS SQL Server and Oracle. Software will support recording It will be possible to use additional features such as mocement/intrusion detection, establishing  connection with video functions between events. It will be possible to use user friendly controls such as Pan, Tilt, Zoom (PTZ) brightness and contrast. Video camera integration will be possible for live video monitoring. Only modifications will be reloaded again. Alarms, trends or loads which are not modified will  continue to work without interruption. It will be able to modify alarms, trend and report servers without rebooting server. It will be possible  to add new configuration, recompişing and apply modification by only reloading suitable server . It will be possible to add, modify, refresh alarms, trends and reports online without rebooting server. Start up and installation manual, user manual and high level manual will be included in technical  manuals. Comprehensive field device manual will be available within online documents for all  protocols and dirvers. Comprehensive documents regarding with configuration and system development regarding with  software will be maintained online.