Construction of Giresun Wastewater Treatment Plant  Tender Dossier Volume 3 Employer’s Requirements  Section 08: Electrical Works  11 of 124   TEDAS-MYD-96-014 Technical specifications for knitted aluminium and steel based aluminium knitted  conductors.   TEDAS-MYD-96-018.A Technical specifications for Insulated Energy cables made from crosswire  polyethylene (XLPE)   TEDAS-MYD-99-033.A Technical specifications for medium voltage cable head   TEDAS-MYD-95-007.C IEC62271-200, IEC 62271-100, IEC 62271-102, IEC 60265-1, IEC 60694, IEC  60281-1, IEC 60044-1, IEC 60044-8, IEC 60044-2, IEC 60529, IEC 60529, IEC 60255Technical  specifications for air insulated, medium voltage, metal clad modular cells   TEDAS-MYD-95-012.B/TEDAŞ-MLZ/99-031.B.Technical  specifications  for  distribution  power  transformers   TEDAS-MYD-2003-006 Technical specifications for metal enclosed low voltage distribution panels   TEDAS-MYD-96-015 Technical specifications for 0.6/1 kV thermoplastic or thermosetting insulated  energy cables.  8.4 Hazardous Area Classification and Ex-proof Equipment All explosion and fire hazards shall be identified and hazardous areas shall be defined in accordance with  international standards by process and electrical engineers of the Contractor in coordination. The plant and  equipment specified for such areas shall be limited as to type and construction by the area classification. Test  certificates shall be furnished for all plant and equipment that constitutes a hazard. Such certificates shall be in  accordance with the relevant standards stated at the end of this item of the Employer’s Requirements.  Whenever on the site an explosion & fire hazard exists, adequate instructions should be given to all personnel  working in the area and notices shall be displayed to warn all third parties of the danger. Such notices should  also advise on precautions to be taken. The Process Engineer is responsible to issue for each unit a list, showing  the data and characteristics of the flammable substances (if any) handled in that unit.  No junction boxes are allowed at hazardous areas. If necessary, Engineer’s approval is required.  Proper electrical equipment and instruments shall be used for the hazardous (Classified) areas (Exd, Exi and  intrinsically safe panel barriers, etc.) 8_Vol3_d4 3_Section 8 electrical works_en_GIR rev6.doc  EUB.02 External type fused earthing breaker  EUB.03 Surge Arresters.  EUB.04 Steel aluminium swallow conductor  EUB.05 Medium voltage cables  EUB.06 Medium voltage cable header  EUB.08 Metal clad medium voltage modular cells  EUB.09 Power distribution transformer  EUB.10 Transformer low voltage panel  EUB.11 Compensation panel  EUB.12 MCC panels  EUB.14 0.6/1 kV YVV (NYY) power, control and signal cables 