Discussion Chain ID: 50267
================================================================================

User asked: Electric meter pulse counting using LLC

I am trying to create an electric meter reading setup for Arduino, and I have been searching for it and almost every posts available is using LDR sensor. <http://www.reuk.co.uk/wordpress/solar/flashing-led-on-electricity-meter/> <https://jonarcher.info/2014/03/arduino-based-electricity-monitor/> And since it is using LDR, the system should be kept in a dark area, or that the LDR is taped to the flashing LED so that no other light source will interfere the sensor. But I wanted to have a different setup, and what I am thinking is: 1. inside the electric meter, tap into the blinking LED 2. From the LED, connect it to an LLC (<https://www.sparkfun.com/products/12009>) 3. From the LLC, connect it to the Arduino 4. Arduino will sense/detect the pulse of the LED. Is this a possible setup? Will it not fry the Arduino or the LLC? Will Arduino be able to detect the pulse? If not, are there any other options? can I use discrete components instead? (I will be the one creating the circuit connection for the LED and Arduino, using resistor, diodes, etc.)

Discussion:
Comment: You know you aren't allowed to open you electricity meter, right? If the company finds out, you're screwed.
Comment: Yes, I am quite aware of that. But this is for a project only. :)
Comment: Relieved to hear that. Then an opto-coupler is the most ideal solution.
Comment: `for a project only` ... is this for a school project? ... if i was teaching your course, i would give you lower marks because of the use of an illegal hack

Answer 1 (0 votes):
When you aren't using the same power supply as the product you are interfacing with, it's usually a good idea of have some form of electrical isolation, which is what the LDR+LED was doing -- there was no way for a voltage spike to reach the Arduino, nor was there any way that different "ground" potentials could cause problems. (Imagine if the ground reference for the meter was floating at a high voltage with respect to earth-ground, but your Arduino power supply's negative line was referenced to earth ground.) A good way to get electrical isolation is with an [opto-coupler](https://en.wikipedia.org/wiki/Opto-isolator), also called an opto-isolator, which is essentially an LED and a photo-transistor inside the same package. The LED side is completely electrically isolated from the photo-transistor side, but light can pass from the LED to the phototransistor. You would connect the opto-coupler so that current passes through the LED side when the pulse happens, and with a pull-up or pull-down resistor on the phototransistor side, which gets pulled down or up (depending on the circuit) when the LED is on. [simulate this circuit](/plugins/schematics?image=https%3a%2f%2fi.sstatic.net%2fiCJ4v.png) - Schematic created using [CircuitLab](https://www.circuitlab.com/)

Discussion on this answer:
Comment: so this means the LED side of the opto-coupler will be the one tapped into the electric meter's LED?
Comment: Correct. Depending on the particular model of opto-coupler, you can put it's LED in series with the meter's LED and hope the voltage drop will not be too much, or you can just replace the meter's LED with the opto-coupler's LED if you are allowed to make that kind of modification.
Comment: Oh okay. How about the connection for the Arduino side? Is it okay if the 5V will come from Arduino Uno's 5V and then the "Arudino input" will be connected to Arduino's Pin 10?
Comment: 5V would come from the Arduino 5V supply, yes. The input would be any digital input pin -- if your code wants to check pin 10, no problem.
Comment: If you plan to put the opto, instead of the led, you may have to add an additional resistor in series with the led. Depending on what value they used in the meter. As the opto uses a IR led, which has a lower forward voltage that the visible led you'd replace.
Comment: Thanks! Any optocoupler you can recommend?
Comment: I won't recommend any particular, except to say that the easiest to set up are the 4-pin. Search the usual vendors, read the datasheets. In the datasheet examine the LED side forward voltage (Input Forward Voltage) and the CTR (Current Transfer Ratio), which tells you the current that will flow through the output side compared to the current flowing through the input side. It all depends on your circuit.
Comment: Alright! Last thing, according to the electric meter I'll be testing, it is 1600 imp/kWh. In getting an optocoupler, is there someting related to this which I need to check on the datasheet of the optocoupler I'll be buying?
Comment: Unless you’re pulling megawatts of power, you don’t have anything to worry about with that pulse rate and any opto.


================================================================================

